A metal plate is installed in the skimmer and the bonding connection is ran through a hole drilled into the side of the skimmer.
However, the product is easily corruptible via everyday occurrences in a residential swimming pool.
When the flow of water into a skimmer is impeded, then the bonding plate is no longer in contact with the water in the pool.
The flow into a skimmer can be easily affected by a low water level condition or by a weir becoming askew (bumped by children, tangled by goggles, a bathing cap, leaves or a twig).
Or a vessel may become a neglected pool, where the water is allowed to drop a few feet, rendering the skimmer bone dry.
In any of these conditions the bonding to the pool water becomes compromised.
24/7 contact must be guaranteed
Regardless of where the water bond is installed, it must guarantee that there will be a 24/7 contact with the water. Safety devices cannot be on sometimes, and operating other. They exist for a purpose. This is not open for debate.
Potential pool leak
Anyone who has ever worked on domestic plumbing, an automobile or ever replaced an o-ring, knows for a fact that they fail. Not if they will fail, but when will they fail. Relying on some caulking and an o-ring to prevent leaks is asking for trouble.
When the o-ring or bonding plate decays due to chemical and salt exposure, how will they be replaced? The bonding wire and retention nut are on the outside of the skimmer, encased in concrete.
A better choice is to locate an in-line water bonding device that can be installed in the water path near the equipment pad. This way it remains accessible and serviceable.
Paolo Benedetti - Aquatic Artist
"Creating water as art."™
Aquatic Technology Pool and Spa
You may contact Paolo Benedetti at:
firstname.lastname@example.org or at 408-776-8220